Air Conditioner Installation for Homes and Offices
Several factors have to considered during the installation of split air conditioner.
Strength of wall to hold the ACThe indoor unit of split AC must be installed on a wall strong enough to hold the unit’s weight.
Proper spacing between wall and AC unitThe indoor unit of split AC requires at least 15 cm of open space surrounding its top and sides for proper air flow.
Appropriate installation height from groundMount the indoor unit of split AC at a height of 7-8 feet above the ground for adequate cooling inside the room
Correct tilt angle of indoor unitWhile fixing the aluminium bracket on wall make sure that the bracket is given a slight tilt angle, so that the indoor unit of split AC, when fitted is also at a slight angle to enable unrestricted flow of the condensed water from the drain pipe.
Correct location of outdoor unitFor proper cooling, mount the indoor and outdoor units of split AC at location away from direct sunlight and water. Install the outdoor unit of split AC in open space so that there is no hindrance to the heat dissipated from the condenser
Proper placement of outdoor unitThe outdoor unit of split AC must be placed on a flat and rigid surface. This unit contains key components of split AC like compressor, condenser, fan motor etc. If the unit is not on a flat surface then it will vibrate excessively, which can lead to the breakage of copper pipes, coolant leakage and compressor/condenser damage. Further, the vibrating unit makes lots of noise which could disturb you and your neighbours.
Right distance between indoor and outdoor unitCorrect distance between the indoor and outdoor unit plays a very important role in cooling. The coolant at very low temperature flows inside the copper tubes between indoor and outdoor units of split AC. There is always some loss of cooling effect to the atmosphere when the refrigerant flows between the units. Hence to reduce this loss, keep the distance between the indoor unit of split AC and the outdoor unit of split AC as minimum as possible. The maximum allowable distance between the indoor and the outdoor units of split AC can be about 15 meters.
Cost for Related Repairs
queueing theory, and comp utational methods
- Monday 9.30 am - 6.30 pm
- Tuesday 9.30 am - 6.30 pm
- Wednesday 9.30 am - 6.30 pm
- Thursday 9.30 am - 6.30 pm
- Friday 9.30 am - 6.30 pm
- Saturday 9.30 am - 6.30 pm
- Sunday Holiday